Buy Eurotherm PID Temperature Controller, 48 x 48 (1/16 DIN)mm, 2 Output Relay, 85 → V ac Supply Voltage /CC/VH/ENG/F Browse our latest. Find great deals for Eurotherm I Temperature Controller With Mounting Bracket. Shop with confidence on eBay!. The i/i are compact high performance 4 digit units for measurement Model i: 48W x 48H x D mm. Display: .. Modbus®, Eurotherm ASCII.
|Published (Last):||7 August 2015|
|PDF File Size:||13.85 Mb|
|ePub File Size:||15.33 Mb|
|Price:||Free* [*Free Regsitration Required]|
Power Isolation The installation must include a power isolating switch or circuit breaker that euortherm all current carrying conductors. Ensure that the installation complies with local wiring regulations. Do not use water or water based products to clean labels or they will become illegible.
Eurotherm i Operating instructions |
Voltage rating Cleaning The maximum continuous voltage applied between any connection eurotgerm ground must not exceed Vac. Process interlocks, including over temperature furnace limits, are implemented using relay outputs.
Universal input selection Two configurable outputs Three internal alarm setpoints Heater failure detection Tactile buttons Customized operator interface. J Alarm 3 is active and it is eutotherm Low alarm.
Repeat for all the parameters you wish to hide or make readonly then return to operator level: It’s a community-based project which helps to repair anything.
Eurothegm will eventually return to the list heading. Always set to Control type Selecting.
Where it is impractical to do this, use shielded cables with the shield grounded at both ends. The latest release of firmware for the nanodac features batch records. Read our latest case studies and Successes. Insert the indicator through the cut-out.
O6 0 Having selected a list heading, press within a particular list. The benefits of two-leg versus three leg power control, in three phase heating applications Download here. Only applies to software version 1. Press and together to return to the HOME display.
Eurotherm 2116I Temperature Controller With Mounting Bracket
While every effort has been made to ensure the accuracy of the information, Eurotherm Controls eurother not be held liable for errors contained herein. In some installations the temperature sensor may become live. Return for repair Low display range exceeded: A universal input enables selection of nine internally stored thermocouple types and the PT resistance thermometer. Mechanical Details Cut-out dimensions Click to enlarge.
All isolated inputs and outputs have reinforced insulation to protect against electric shock. Alarm Ack input Logic only D Functions: The parameter in the N0 list applies a fixed offset over the whole display range. Return for eufotherm Power failure. Stuck button, or a button was pressed during power up. Return for repair Error 4: Where condensation is likely, for example at low temperatures, include a thermostatically controlled heater in the cabinet. Keep pressing to increase the value.
Three internal alarm setpoints are provided – configurable as high, low or deviation alarms. Return for repair Error 3: With a live sensor, all cables, connectors and switches for connecting the sensor and non-isolated inputs and outputs must be mains rated. Alarms can still be configured and flashed as messages in the main display but they will not be able to operate eurtherm physical output.
Keep pressing to decrease the value.
Eurotherm i Manuals
It may be necessary to fit a filter across the relay output to suppress conducted emissions. Recommended minimum spacing of indicators in both sizes Panel cut-out OP1 48mm 1. Other parameters are locked away under password protection.
Press to enter configuration level.