IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. 5. Voltages limited by arresters. Arrester power frequency witstand voltage. Resulting . An allowance of at least 5% (IEC ) is recommended. With this.
|Published (Last):||28 May 2011|
|PDF File Size:||2.44 Mb|
|ePub File Size:||18.79 Mb|
|Price:||Free* [*Free Regsitration Required]|
Selection and application recommendations. In Annex J, some aspects regarding the old type of SiC gapped arresters are discussed.
The Redline version is not an official document, it is available in 06099 only and provides you with a quick and easy way to compare all the changes between the official IEC Standard and its previous edition. Please note that the selected standard is invalid.
Annexes H and I present comparisons and calculations between old line discharge classification and new charge classification. Message to your colleague. Surge arresters – Part 5: The following test report forms are related: It is likely, however, that for some systems, or in some countries, the requirements on system reliability and design are sufficiently uniform, so that the recommendations of the present standard may lead to the definition of narrow ranges of arresters.
What is a standard? Sustainable Development Goals and standardisation, how do they connect?
Your shopping cart is empty. Surge protective devices connected to telecommunications and signalling networks – Performance requirements and testing methods.
Preview Abstract IEC Valid Buy this standard. Our prices are in Swiss francs CHF. Subscribe on standards with our subscription service.
Selection and application recommendations Article no: This edition includes the following significant technical changes with respect to the previous edition regarding the new surge arrester classification introduced in IEC It applies 600099 gapless metal-oxide surge arresters as defined in IECto surge arresters containing both series and parallel gapped structure — rated 52 kV and less as defined in IEC and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines EGLA as defined in IEC Contact us svenska Login.
IEC RLV | IEC Webstore
SS Valve type surge arresters – Terminology. We accept ic major credit cards American Express, Mastercard and VisaPayPal and bank transfers as form of payment. Report error on page. This edition constitutes a technical revision. The standard is now in your shopping cart.
Read more about SIS Subscriptions. Do you need a multi-user copy?
The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any 55 installation and the selection of characteristics resulting from prior practice may be continued. Subscribe on standards – Read more. Related publications IEC Shopping cart Close cart 0, foreach: Selection and application recommendations Status: This third edition cancels and replaces the second edition published in Typical maximum residual voltages are given in Annex F.
IEC | IEC Webstore
When you use our service you can be assured the latest editions and easy access. Fuses and other overcurrent protection devices Substations, surge arresters.