Product category: PLCs – Omron – C – Omron CH-LK (CHLK) This unit is fully tested prior to. Q: Can CH-LKV1 Host Link Unit be used with CS1-series Programmable Controllers?. CH Units that use the CPU bus, SYSMAC LINK Unit, CHW-SLK23/24 ( wired) CHW-SLK13/14 (optical). Controller Link Unit, CHW-CLK21 (wired ).
|Published (Last):||18 December 2009|
|PDF File Size:||10.59 Mb|
|ePub File Size:||19.5 Mb|
|Price:||Free* [*Free Regsitration Required]|
C Series Host Link Units. This may or may not be an issue if they are mismatched Prev 1 2 Next Page 1 of 2. The PLC configuration does not matter. The manual in the link I posted above describes v200h functions.
Omron CCNEU Programming Cable, For Use With CH-LK PLC, 6 ft Buy from Cross
c2000h With the information you have provided, there is no way for us to tell. Try to put il elsewhere. You should verify the cable. What is the part number of your back plane? Jay and Bob, Thanks for the feedback! This is common Omron serial settings. One says v200h to use those slots, the other says it’s OK but you will lose some functionality on the peripheral port.
If possible, which cable I have to use? I also tried with this cable LK Coputer I will check the cable one more time!
Sign In Sign Up. Thank you for your reoly! Neither of them are V1’s. This is basically the same as the rack mounted unit you have. Go To Topic Listing Omron. It is a pre-Alpha series. Posted 14 Nov edited. On the older ones, it was only intended for the hand held programmer.
Then the PLC cannot connect to Pc. Try turning if OFF. I have l201 with an ch-lkv1 but lkk201 is the same. But there’s still no RCV light Please help me! Remove all the modules from the rack and try the Host Link in another slot. I have checked the cable carefullly, the cable should be ok. Posted 20 Nov Started by sokhanh13 Nov Maybe the backplane is bad. It’s on page 9 in the manual.
Sign in Already have an account?
Omron SYSMAC C200h-lk201 Host Link Unit C200HLK201
This is a node address. Also the command level is set for a custom application for full read and write. Last week, the cpu couldn’t power on, so I have replaced with a new CPU. If your application is not sending an address and a calculated FCS then it will not communicate with pin 3 set to ON.
In any case, look here: Could anyone help me how to check and slove this ll201 Posted 21 Nov Edited 16 Nov by sokhanh. Posted 13 Nov After revisiting this I found conflicting information in the c20h0. You need to be a member in order to leave a comment. Edited 15 Nov by sokhanh. I have blown internal circuit board fuses on some of the older CH’s by trying to use that port.
I did notice that both of his modules are in the restricted slots. Pin 3 on the back may be the problem depending on how your custom application was programmed. Sign up for a new account in our community.
Create an account or sign in to comment You need to be a member in order to leave a comment Create an account Sign up for a new account in our community. The 25 pin connector would run into the bottom of those peripheral units if you used these slots.
Share this post Link to post Share on other sites. No electrical or logical restriction for using these slots with CH-LK Be careful what you plug into it. Can I move the host link to other slot of BB?